Flowserve Master Station II (4100) Driver
2 Wilshire and Wilshire are registered service marks of Wilshire Starwood Hotels & Resorts Worldwide, Inc. , 3, Station Casinos, , o Scientific Games Corp., Class A , 1, o Shuffle Master, Inc. 37, 1, 3 o CACI International, Inc., Class A 4, o Career Education. 9 DTM LICENSING Flowserve Corporation 2 have been authorized by those responsible for the safety of the plant to perform the necessary work and who can. Purpose User Safety Product Description 5 2. .. actuators equipped with Modbus can be controlled via Flowserve Limitorque s Master Station II or III.
|Supported systems:||Windows 2K, Windows XP, Windows Vista, Windows Vista 64 bit, Windows 7, Windows 7 64 bit, Windows 8, Windows 8 64 bit, Windows 10|
|Price:||Free* [*Free Regsitration Required]|
Flowserve Master Station II (4100) Driver
See chart below for maximum number of drive sleeve turns for each unit size.
Flowserve Master Station Ii Firmware Driver Download
The Flowserve Master Station II (4100) Shaft Bshown in Figure 3. Do not use a variable speed electric drill for setting the limit switch in an explosive environment. When setting the limit switch rotor segments cams using a variable speed electric drill, do not run drill at speeds higher than RPM. Operating the drill at high speeds can damage the gearing within the limit switch. Open the Controls Compartment Cover refer to Figure 5.
Put the actuator into manual operation. Use the handwheel to operate the valve in the open direction.
While operating the valve, note the direction of the Intermediate Shaft B corresponding to the rotor or rotors to be set. When the valve is fully open, close it one turn of the handwheel to allow for coast of moving parts or refer to the valve manufacturer setting requirements.
ValveSight DTM Quick Start Guide For Logix Positioners with HART
Push in the Setting Rod A and turn one-quarter turn. The rod will latch in this depressed position.
Refer to the applicable wiring diagram for contact development. The limit switch contact is closed when the rotor is engaged with the Flowserve Master Station II (4100). If the rotor to be set has not turned 90 degrees to operate the plunger, turn the intermediate shaft in the same direction as noted in Step 2 until the rotor clearly trips the switches.
This rotor is now set correctly. Before moving the valve, depress and turn the Setting Rod A one-quarter turn to the spring released position. Insert a screwdriver into the intermediate shafts to ensure that they will not move. Do not Flowserve Master Station II (4100) the valve when Setting Rod A is in a fully depressed position.
Loss of contact setting will occur and the setting rod will be damaged. Operate the valve by handwheel to fully close position; reverse direction by one turn of the handwheel to allow for coast of moving parts or refer Flowserve Master Station II (4100) the valve manufacturer setting requirements.
Flowserve Master Station Ii 4100 Firmware 2.53 Driver Download
Set the other rotors by following Steps 4 Flowserve Master Station II (4100) 6. Remove Nuts piece 8 and Fillister Head Machine Screws piece 5, for a total of two fasteners on each side of the switch. Remove complete contact assembly from the back plate. Rearrange cams on the camshaft to produce the required combination of contacts.
Replace contact assembly on back-plate ensuring that the registers fit correctly and secure with the machine screw and nuts Set limits according to the procedure above. Confirm that the limit switches are set properly prior to disassembly and removal of the UEC-3 and related components. Confirming the settings will allow for installation of the UEX Electronic Controller without requiring Flowserve Master Station II (4100) reset of the limit switches.
Turn off the power to the actuator.
Download Flowserve Master Station II Firmware for OS Independent
Open the Controls Compartment Cover. Cut and remove all wire ties from wiring that is connected to the UEC-3 assembly pc C Disconnect the incoming power from the Interconnect Board.
Disconnect the Motor leads and Heater leads from the Interconnect Board. Disconnect the Pushbutton Station ribbon cable from the Interconnect Board. Label all customer wiring and disconnect from the Interconnect Boards. Make sure you remember what slot you put the USB Driver, in case you unplug and Flowserve Master Station II (4100) in a different slot you will need to install the driver for the different slot.
Right Click on My Computer and select Manage. You will see a widow on the right of the page called Device Catalog. At the bottom of the page, click on Update. Right click on the My Network icon.
Check with the modem manufacturer to select the correct Access Mode. For example, using cookies with the Websites allows you to come back to the Websites or browse from one page to another without having to resubmit your preferences and other information.